• This field is for validation purposes and should be left unchanged.

### Under which conditions can antiscalants cause RO membrane fouling?

Reverse Osmosis Antiscalants can cause membrane fouling in Reverse Osmosis systems under the following conditions: Fungal growth in the antiscalant –  some antiscalants contain impurities that can provide the necessary nutrients and ...

### Can I use citric acid to descale/clean a reverse osmosis (RO) Membrane?

Citric acid is an organic acid that is often used for removal of calcium carbonate scale and is often mistakenly believed to be effective at dissolving iron fouling.  It actually has only marginal impact on iron hydroxide deposits, and is ...

### When do we know if the cleaning of our Reverse Osmosis plant was successful?

Once the RO membrane system is placed back online after CIP, you can get a relatively good idea by comparing post-cleaning feed pressures and differential pressures for each stage to pre-cleaning values.  The most reliable method would be ...

### What is the best post-CIP flushing procedure in Reverse Osmosis systems? How do we know when flushing after a cleaning is done?

Always flush your membranes with RO permeate until the pH measured at the waste end is within a pH range of 5 – 9.  You can then proceed to flush with feed water until the pH of the water exiting the RO membrane system is similar to the ...

### Can we send the CIP solution to our deep injection well after cleaning our Reverse Osmosis membranes?

No, if a high pH RO cleaning solution is mixed with RO brine, it would result in severe scaling.  Always consult with your hydrogeologist before sending any solution to the deep injection well. See also: What is the procedure for cleaning ...

### Our RO plant doesn’t have a neutralization tank for our spent CIP solution. Can we just neutralize while circulating through the membrane system?

That is not recommended.  A high pH cleaning solution is designed to dissolve membrane foulants and scales that are soluble in basic conditions.  A low pH cleaning solution is designed to dissolve membrane foulants and scales that are sol...

### Can we send our CIP solution direct to the waste water treatment plant after cleaning our Reverse Osmosis System?

No, pH extremes can be very disruptive to bacteria and can upset the operation of the wastewater treatment plant.  The RO cleaning solution should always be neutralized prior to sending to a wastewater treatment plant.  The solution is us...

### We recently installed new RO membranes in our system and observed that the permeate water tested positive for coliform bacteria. Is it possible in your experience that RO membranes could be damaged during installation and cause contamination of the water distribution system by bacteria and pathogens?

It’s unlikely that the RO membranes were damaged inadvertently during installation. While it’s possible for there to be manufacturing imperfections that allow pathogens such as viruses and bacteria to pass through, it’s not common. In...